Once super-heated refrigerant gas leaves the compressor it travels through the suction line to the compressor. The compressor in this example is a reciprocating compressor and the cycle can be referred to as the vapor compression cycle.
To compress the vapor, it must be put in an enclosed container, then, the container must be made smaller, forcing the molecules of the gas closer together, or, compressing them.
A few things change when you compress a gas, the volume goes down, the pressure and the temperature go up.
If I took a frictionless compressor and put 1 cubic foot of R404A in it and compressed that gas to .33 cubic foot the following would be the outcome:
Compressing the volume in a ratio of 3 to 1 (1/.33=3), the pressure increased 110.5 psi (pound per square inch), and the temperature increased 72.5 degrees Fahrenheit!
This is a pressure ratio of 3.17 and a temperature ratio of 2.65
Considerable change in the properties for a relatively small compression ratio.
Notice the ratios are not the same, volume = 3, pressure = 3.16, and temperature = 2.65. These properties change based on the physical aspects of the individual refrigerant and will be different for every compression process.
A basic reciprocating compressor will have the piston and cylinder just like the example above except with a few more components to put work into the system.
The compressor needs a suction valve to open when gas is coming into the cylinder, and a discharge valve that opens when gas is leaving the cylinder.
The valves are reeds or spring loaded disks, reeds being more common due to cost. Below is a sketch of the example compressor with the suction and discharge reed valves.
Reed is a flat piece of spring steel which lays flat over the suction and discharge ports. As the picture indicates, the valves open when there is a difference in pressure, they spring closed when the pressure is equal.
If you lose the suction or discharge valve, the suction and discharge pressure will run about the same.
If you lose the rings in a compressor, but not the valves, oil sump pressure spike, discharge pressure will be low.
Evaporating and the TP Chart
The refrigerant leaving the metering device is at a much lower pressure than the liquid line delivering it to the metering device. The liquid is pushing forward into the evaporator coil and rapidly expanding (hence the term “expansion-valve”) into droplets and vaporized refrigerant.
The droplets shed down the tube walls picking up the heat energy from the external load (heat) being applied to the exterior of the evaporator coil. As the droplets absorb enough energy (latent heat of vaporization) they transform into vapor (boil). The refrigerant will be in a state of “saturation” (equal parts of vapor and liquid) until the last drop of liquid is boiled away.
The pressure on the low-side is dictated from the vaporization process and will remain constant while the continuous boiling occurs. This is the saturation pressure and it has an associated saturation temperature that goes with it. If the low side, (suction) pressure is reading 92.7 (~93) psig on your manifold, and the refrigerant is 404A, then you know the evaporator is operating at 44 F per your TP (Temperature Pressure Chart).
But now you put your thermometer on the suction line leaving the coil (because you usually can’t check the coil directly) and the temperature is 54 F, what up with that?
Coils are designed with a function called “super-heat” built in. It is a section of coil exposed to the load that allows the refrigerant gas to be further heated up by the heat available in the load. This function, the super-heat function, protects the compressor from liquid flood back, a dangerous condition that will severely damage the compressor.
As a note, here, expansion valve manufacturers usually pre-calibrate new thermostatic expansion valves to operate at 10 degrees Fahrenheit of super-heat, I suggest you don’t adjust it unless you REALLY, REALLY, know what you are doing.
If you could measure the evaporator it still wouldn’t read 44 degree directly since you must account for all the interference from the blower/heat-load interacting with the coil surface, a likely reading would be between 46 F and 54 depending on where you take it and how well the reading is insulated from the process. Manufacturers use a device called a “thermos-well” to obtain an approximation of the coil temperature when needed. The thermos-well is a tube inserted into the refrigerant line which is partially protected from the load and can readily sense the coil temperature with a thermocouple or temperature gauge. (See below.)
After the refrigerant leaves the condenser, (covered in an earlier post), the refrigerant is delivered, via the liquid line, to the metering device.
The metering device has two jobs, provide the necessary pressure drop, and provide the correct amount of refrigerant to the evaporator to handle the design load.
‘Design’ is in bold italic because the metering device, no matter the type, is matched to the load conditions and will only perform properly in a small operating window.
I like to lump the metering devices into two categories, fixed metering devices, and dynamic metering devices.
Fixed metering devices operate in a very small range and are extremely susceptible to operating conditions. The basic design of a fixed metering device is based on a restriction of the flow causing a pressure drop in the line while maintaining enough of a through put that some refrigerant makes it into the evaporating coil.
Fixed metering devices are inexpensive solutions but also inefficient and have limited capability. You will likely see a decline of fixed metering devices as the demand for more energy efficient design rises.
Fixed metering devices do not respond to the load per say, only to the differential pressure between the condenser and the evaporator.
Some fixed devices rely on an orifice, or ‘seat’ and an adjustable ‘trim’ which is a tapered stem that, when held at the seat, creates a restriction that is adjustable.
Another type of fixed metering device is the capillary tube, a very common type of metering device in small appliances. The capillary tube is a long length of tubing with a small diameter bore inside. The small bore and length, the bore determines how much refrigerant will pass, while the length, determines the pressure drop. Word of caution, if you cut a capillary tube, its ruined, the length and continuous, unobstructed bore, are critical! Patching it back together will change the characteristics of the tube, usually resulting in a very different performance.
A third type of fixed device is an orifice tube, commonly found in cars. The orifice tube is a metal tube that sometimes contains a removable inlet screen and a plate with a very small hole in it (the orifice), the very small hole controls the amount of refrigerant and causes the needed pressure drop. Due to the itty-bitty hole, the orifice tubes plug up easily. Best way to spot this is to look for frost just after the tube or temperature below the expected evaporator temperature. (Assuming the unit has the proper charge in it.)
A fourth, yes there’s another, is the piston orifice, the piston contains the small hole just like the plate in the orifice tube, but the piston is free floating in a large close coupled nut assembly. The piston moves forward during operation, then relaxes when flow stops, this action allows for the system to equalize the high and low side pressures lowing the compressor starting torque. Warning, these assemblies are usually brass brazed onto copper tube, they will gal, strip, cross thread, and twist the tube if not properly serviced, never force it together, keep it straight, do not over-tighten, and ALWAYS use a backup wrench to hold the swivel nut!
Below are some sketches of the basic configurations of fixed metering devices:
Dynamic Metering Devices try to adapt to changes in load by one of several means, pressure, level, or temperature.
Pressure controlled metering devices are called automatic expansion valves. The valve is an adjustable spring loaded diaphragm against the evaporator pressure with a tension that corresponds to the middle of the expected range of operation. When the evaporator pressure fluctuates with load, the valve can open or close to compensate within a narrow range. These were found a lot in old window, PTAC, and purge units, and look like right-angle valves with a silver tank on top, the adjustment was usually a slotted screw sticking out the top. Note; if it leaks around the screw, its bad.
Metering devices that respond to level changes are used only in flooded evaporator arrangements and are usually configured with a float to respond to liquid level changes. (There were some electronic level sensors but they never became very popular.) The float is installed in a ‘side’ chamber of the evaporator, one for serviceability, and second, for level stability. As the level went up or down the float would move up or down and either feed refrigerant in, or cut it back. Floats could also be used to send a signal to a pneumatic or electronic controller that could actuate a remote valve to achieve the same purpose. The pivot pins in these designs wear very quickly and periodic replacement is a must. Most side chambers could be isolated and re-built, but some units must have the entire charge removed to work on the float.
Temperature controlled metering devices are called thermostatic expansion valves and are used in air-conditioners, spot coolers, window units, chillers, refrigerators, freezers, etc. The most common temperature controlled expansion valve (TXV) is controlled via a sensing bulb full of a captured refrigerant charge. The bulb senses the temperature of the suction line. An increase in suction temperature opens the valve and increases the refrigerant flow to the evaporator, a decrease in the suction temperature cuts back the valve due to the expansion and contraction of the captured refrigerant in the bulb and power assembly. There are both balanced (pressure compensated) and unbalanced (spring only compensated) valves.
EXV, or electronic expansion valves, are thermal expansion valves with motors attached instead of power assemblies. They have a controller that senses the super-heat and adjust the valve accordingly. EXV valves can modulate the refrigerant flow very accurately and are the most efficient solution for many applications.
Condensing and the TP Chart
First, let’s hit condensing. In a refrigeration machine, the condenser, has three jobs, de-super-heating the hot gas from the compressor, condensing the refrigerant back into a liquid, and sub-cooling the refrigerant to maintain a solid flow of liquid for the metering device (expansion device, TXV, capillary tube, EXV, etc.)
De-super-heating: The gas leaves the compressor at the highest temperature in the system. The excess heat from friction and compression must be removed to approach the saturated (condensing) temperature. This is usually done in the first section of the condenser. In the illustration below, from point 2 to point 3, the fan, forcing air across the condenser, lowers the refrigerant temperature to 100 Fahrenheit from a discharge temperature of 160 Fahrenheit.
The lowering of the temperature by removing the heat from the refrigerant is a ‘sensible’ cooling process where no change in state of the refrigerant occurs (it’s still 100% vapor).
Condensing: Once the refrigerant reaches its saturation temperature, the refrigerant condenses, during which, the energy being removed from the refrigerant is spent turning the refrigerant into liquid, the temperature and pressure do not change during the condensation phase. The condensation phase is a latent cooling process. The refrigerant exists in the condenser in varying states of liquid and vapor until only liquid remains.
The resulting condenser pressure is the saturation pressure and dictates the pressure of the ‘high side’ of the system.
Sub-Cooling: When only liquid remains, another sensible process can begin, it is called sub-cooling. Sub-cooling is further lowering the temperature of the liquid refrigerant below its saturation temperature, the pressure, does not change.
The TP table, temperature pressure table available free from most any refrigerant manufacturer website, is a list of the saturation pressures and temperatures for individual refrigerants. (There are also apps for that!).
In the above example, the refrigerant is 404a, and the condensing temperature was 100 F, the pressure would be 235 psig (pounds per square inch gauge or what your manifold would read). See below:
However, if the gauge was reading, 218 psig, then out condensing temperature would be 95 F.
Say the pressure is 218 psig, and you read the line temperature leaving the condenser and it is 100 F?
The higher than saturation temperature at the liquid line leaving the compressor indicates a problem, could be under-charge, air in the system, or some reason the unit isn’t condensing the refrigerant (double check your temperature reading device against boiling water to make sure it reads correctly should read 212 F in the water).
So, now what if the temperature is reading below 95 when the pressure is 218 psig? That would mean there is sub-cooling occurring, when the liquid is being cooled below its saturation temperature.
If we see about 90 F on the liquid line, the condenser is probably doing its job, marginally anyhow.
Condenser sub-cooling range varies based on design but it is required to have enough sub-cooling to maintain a liquid full liquid line regardless of the pressure drop between the condenser and metering device (expansion valve).
The typical range will be from 5 to 15 degrees depending on the type of metering device, with 9-12 being common for TXV and EXV systems (always check with manufacturer data) and higher for capillary tube systems (which vary with load considerably)
Low sub-cooling ranges are usually reserved for close couple units where there is no appreciable pressure drop.
The sub-cooling is always taken just after the condenser, if there is a receiver or suction heat exchanger the temperature after those devices indicates how they are working not the condenser.
Basic Refrigeration Cycle
Basic Vapor Compression Cycle, the Carnot CycleFour main elements are required to complete the basic refrigeration cycle, a compressor, a condenser, a metering device (expansion valve in this case), and an evaporator, all labeled below in the system diagram along with connecting components.
Below is what the perfect system, Carnot system, looks like compared to a practical system on a diagram called a “Pressure-Enthalpy Diagram”. (Enthalpy, for this brief introduction, can be considered energy).
The numbers in the above diagram coincide with the description numbered 1-8 above for each stage of the cycle and the refrigerant condition.
It stands out, that the practical cycle is more outside the saturated region and rises above and below the Carnot cycle. The differences are driven by the efficiency of the physical equipment and materials used to apply the process.
The lower line, dubbed 7, is the evaporator line, it is lower because the material used in evaporators isn’t 100% effective at transferring the heat. Evaporators must be designed below the cycle temperature that is wished to achieve.
Same as for the condenser, location 3,4, and 5, but in the opposite direction, condensers must run hotter than the theoretical cycle to work.
From point 1 to point 2 is compression, on the Carnot cycle, the compression takes place with no losses, on the practical cycle, it extends out past the Carnot due to inefficiency that generates heat and volume losses.
Point 5 must extend into the liquid region to ensure that the expansion valve function correctly.
At point 6, The Carnot cycle would deliver liquid at 100% quality to the evaporating cycle, where the practical system must accept liquid at a quality of 12-18% (vapor fraction) this reduces the over-all refrigeration attainable per cycle, which is less efficient.
That wraps up the basic refrigeration vapor compression cycle. More details will be explored in later posts.
What is Cooling?
What Happens When Something is Cooled?Seems simple enough we may be compelled skip this post and move on to something less elementary, but when this question was posed to me, just of late, I had to take a pause, all the mechanics of the fluids interacting and transferring the energy from one point to another made me realize, I don’t have a simple answer for that, so I thought I would reduce the process to its simplest form.
Cooling is when we use a means to remove the energy from an object, or substance, to lower the bulk temperature of said object or substance.
As simple as I can put it, but I don’t think that statement will mean much to most who read it. So, here I will try to paint a broader picture as painlessly as possible.
To discuss what happens when something is cooled, we may need to look at what makes things hot while avoiding a physics lesson. Consider that when we add energy, in the form of heat, to an object, the temperature of that object increases.
The excess energy, or heat, we added to the object remains stored up in the object we heated until we give it an avenue to escape.
It’s a physical law that energy will travel from a higher point of energy to a lower point of energy, or in the case of heat, heat will always travel to a lower point of heat (notice I said “lower point of heat”, not “cold”, cold is a sensation, an individual perception or point of reference).
Given our object, we just heated up, if it was surrounded by air at a lower temperature, the object would cool by convection moving the heat energy to the air surrounding the object until the object and the air where the same temperature, this is called equilibrium, the process is called cooling.
The concept herein is foundational to refrigeration, if the evaporator isn’t a lower temperature than what it is cooling, then it won’t work, if the condenser isn’t hotter than the air or water cooling it, then the condenser won’t work.
I worked for over thirty years in the HVACR industry. I have designed, installed, serviced, and trouble shot units of various types throughout the years. The posts here are information based on that experience, I hope you find them useful. If you have a different experience, please comment.